Floatless Switch, Compact Plug-In Type61 F-GP-N 61F-GP-N AC100
- 61F-GP-N AC100
- Package Qty.
- Ship pack of
- Withstand Voltage
- AC2000V 50/60Hz 1min
- Reset Resistance between Electrodes (ohm)(Recommended Value)
- About 15-infinity
- Rated Voltage (V)
- AC100 (50/60-Hz common use)
- Tolerable Voltage Fluctuation
- Rated voltage of 85-110%
- Ambient Humidity
- 45 - 85%RH
- Weight (g)
- With LED operation indicator
- Pin Type
- 11 pins
- Response Time
- Operation: 80 ms or less
160 ms or less at the time of return
- Cable Length (m)
- Below 1k
(600V0.75mm 3-2fully insulated processing cabtyre cable
- Controlled Object, Using Condition
- Common clean water, sanitary sewage
- Electrical:More than 100,000 times
Mechanical:More than 5 million times
- Insulation Resistance (Mohm)
- More than 100 (with DC500V mega)
- Current between Electrodes
- 1 mA or less of AC
- Voltage between Electrodes
- Outside Dimension (mm)
- Height 49.4x width 38x depth 84
- For general use
- Operating Ambient Temperature (deg C)
- -10 - 55
- This product is manufactured in Japanese standards. Please check the specification before you order., Insulation resistance and electric strength are the value between power terminal and terminal electrodes, between power terminal and terminal, and between contacts between terminals.
- Dynamic Resistance between Electrodes (ohm)(Recommended Value)
- 0 - about 4k
- AC250V 3A (resistance load)
AC (inductive load cos phi =0.4) 250 V1A
- CE standard conformity
UL/CSA standard certified product
- With LED operation indicator Output ensures independent 2c connection
Customers Who Viewed This Item Also Viewed
| 5 star
| 4 star
| 3 star
| 2 star
| 1 star
6 Customer Reviews
The reviews are automatic translation.
It is for exchange.
On 2017-03-29 18:03:53
Correspondence, goods, is satisfied with the packing both. Also I will try to buy.
On 2016-05-16 09:07:12
Start and stop for the water level electrode of automatic operation
On 2015-03-10 18:21:14
Early until the arrival from the order, have survived can be used with confidence because manufacturers goods.
Replacement of mechanical parts
On 2014-07-14 20:09:03
In particular, you can use without any problems. Cheaply from the manufacturer, we want to use if it so early also accommodate other parts.
It is used for the water level of the raw water tank of the factory.
On 2013-12-18 17:12:50
I replaced it due to deterioration of years It is used without problems.
Used as part of pump control panel
On 2013-07-24 16:49:02
It is a component of the control board for agricultural water and malfunction occurs when it receives thunder etc. I am thankful that I can use 100V 200V. Since it is part replacement of the existing control panel, it is not so much to be broken, but it is bought, even as a spare part.
Customers Who Bought This Item Also Bought