Set Terminal Block T30 T 30 C02
T 30 C02
Ship pack of
This product is manufactured in Japanese standards. Please check the specification before you order.
Compatible Electric Wire (mm2)
Group Terminal Block
45 - 85%
Number of Poles
2.2 - 2.8N･m
Dimensions B (mm)
-20 To 55 degree c ( However, no dew condensation or icing )
40 deg C or less (rise-in-heat value of electric conduction metal fittings)
terminal base: phenol terminal thread-part: iron (zinc galvanizing chromate treatment) plate conducting: brass (nickel plate) register seal: fiber covering: polycarbonate
Rated Impulse Withstand Voltage (kV)
Rated Insulation Voltage (V)
2500V, 1 minute
Dimensions A (mm)
JIS C2811(industrial terminal block)
Rated Value (A)
2) Terminal Screws
M5x12+/- self rise
Connectable Wire (mm2)
3.5, 5.5, 8
Maximum Current (A)
2-30 5.5mm 2-40 8mm 2-50 Insulation Resistance (Mohm)
100 and above (between each live parts, or between each live part and metal mounting plate)
Customers Who Viewed This Item Also Viewed
5 Customer Reviews
The reviews are automatic translation.
On 2017-11-11 18:22:43
I always use it.
I think that there is no problem.
I will continue to use it.
Distribution board from generator on site
On 2015-02-28 18:17:03
Easy to use
Relay wiring between the testing machine and the device under test
On 2014-11-19 10:16:34
For wiring, use a cord with a crimp round terminal normally. I screw it, but as you move the cord, the screw loosens and it moves soon and it seems to come off. Although it is a structure to suppress the screw with a mountain of crosses when seeing it, since the contact area is small, the power of holding down is insufficient. So I use all the screws instead of ordinary sems screws, flat washers, spring washers. Also, since it is an iron screw, the electric resistance is large, and if you want to say it, the resistance loss should be reduced by the brass screw.
Independent solar power generation
On 2014-04-21 08:17:56
Truly Kasuga Electric, a sense of security when crimping terminals are tightened! It is! Best
For wire connection terminal branch
On 2014-01-10 12:13:27
The screw part is weak, and when it is fitted or removed many times, the screw will become difficult to tighten. I feel that the strength of the screw part is weak.
Customers Who Bought This Item Also Bought