Set Terminal Block T30 T 30 C12
- T 30 C12
- Package Qty.
- Ship pack of
- This product is manufactured in Japanese standards. Please check the specification before you order.
- Compatible Electric Wire (mm2)
- Group Terminal Block
- Connectable Wire (mm2)
- 3.5, 5.5, 8
- Relative Humidity
- 45 - 85%
- Number of Poles
- Weight (g)
- Clamping Torque
- 2.2 - 2.8N･m
- Temperature rise
- 40 deg C or less (rise-in-heat value of electric conduction metal fittings)
- terminal base: phenol terminal thread-part: iron (zinc galvanizing chromate treatment) plate conducting: brass (nickel plate) register seal: fiber covering: polycarbonate
- Maximum Current (A)
- 3.5mm2-30 5.5mm2-40 8mm2-50
- Rated Impulse Withstand Voltage (kV)
- Rated Insulation Voltage (V)
- Dimensions B (mm)
- Withstand Voltage
- 2500V, 1 minute
- Dimensions A (mm)
- Conformity Standard
- JIS C2811(industrial terminal block)
- Rated Value (A)
- Terminal Screws
- M5x12+/- self rise
- Insulation Resistance (Mohm)
- 100 and above (between each live parts, or between each live part and metal mounting plate)
- Ambient Temperature
- -20 To 55 degree c ( However, no dew condensation or icing )
Customers Who Viewed This Item Also Viewed
| 5 star
| 4 star
| 3 star
| 2 star
| 1 star
4 Customer Reviews
The reviews are automatic translation.
Distribution panel from the generator in the field
On 2015-02-28 18:17:03
Easy to use
Testing machine and the relay wiring to the equipment under test
On 2014-11-19 10:16:34
Usually use the code that wearing a crimp round terminals for wiring. It screwed, but if moving the code will likely off moving quickly loose screw. See when the screw is a structure that keep with the cross of the mountain, the power of suppressed since the contact area is small and insufficient. So I use instead of the whole of the screw ordinary SEMS or flat washer, the spring washer. In addition, since the iron screw large electrical resistance, we should see more of the brass screw reduces the resistance loss Speaking greed.
Stand-alone solar power generation
On 2014-04-21 08:17:56
Indeed Kasuga Electric Works, a sense of security when tightened mounting crimp terminals! !
Electric wire connection terminal branch
On 2014-01-10 12:13:27
Weak threaded portion, or fit a number of times, it will become difficult interference screw and or removed.
The strength of the threaded portion will feel weak.
Customers Who Bought This Item Also Bought